In the central air-conditioning repair process, it is inevitable that central air-conditioning disassembles and devices, then how to disassemble the central air-conditioning ? Next we will take a look at how to disassemble the central air conditioner .
How to disassemble the central air conditioner
1. At least two or more persons (a skilled refrigeration repairman plus one deputy);
2. A set of refrigeration repair tools, as well as fixed expansion screws for indoor and outdoor machines;
3, a seat belt.
Second, disassemble steps
1, recycling refrigerant
Whether in winter or in summer, the refrigerant in the air conditioner must be collected in the outdoor unit. Before starting the dismantling, start the air-falling device and set the cooling state. After the compressor is in operation for 5-10 minutes, after the cooling state is normal, use a wrench to unscrew the cap on the external liquid pipe and the gas pipe connector, and then close it with the hexagon socket. The stop valve of the high-pressure tube (fine), after 1 minute, the tube surface condensation, immediately close the low-pressure tube (thick) cut-off valve, the same rapid shutdown, unplug the power plug, tighten the fuse cap with a wrench, and thus complete the recovery of refrigerant. (If it is winter, you should use a warm towel to cover the temperature sensor probe of the indoor unit first, then control the cold state to set the power on.) You can also use the forced start button on the indoor unit to boot, and observe whether the indoor and outdoor machines still have Other faults. Avoid troubles after relocation.
2, remove the indoor unit
After the refrigerant is recovered, the indoor unit can be disassembled. Use a spanner to unscrew the indoor unit's connection lock nut, and use the prepared sealing sodium to wrap the thread of the indoor unit's connection joint to prevent the connector's thread from being damaged in handling. Then use a cross to remove the control line. At the same time should be marked to avoid mistakes in the installation. If the signal cable or power cable is connected incorrectly, the external unit will not operate or the machine will not be controlled. The internal machine hanging plate is generally fixed and relatively difficult to unload; after unloading and removing the hanging plate, it is placed on the flat cement floor and then gently patted and corrected.
3, split the outdoor unit
Dismantling the outdoor unit shall be dismantled by a professional refrigeration serviceman while ensuring safety. After unscrew the external machine to connect the lock mother, apply the prepared sealed sodium spinner to secure the thread of the outbound machine connector. Use a wrench to loosen the fixing screw of the outer machine foot. When laying down the outdoor unit after dismantling, it is best to use a rope to hang it. When releasing, pay attention to balance, avoid vibration, bump, and pay attention to safety.
The air conditioner should be slowly taken over and the four plugs should be used to Seal the four ports of the connecting pipe to prevent dust and moisture from entering the air. The plug is good, and finally tied with plastic bags, plated for easy handling.
Above about how to disassemble the central air conditioning is a simple introduction here, and I hope to help you. For more information, please visit this website. Stay tuned.
Central air conditioning
Silicone o-rings are based on silicon, an element derived from quartz. To create this class of synthetic elastomers, pendant organic groups such as methyl, phenyl and vinyl are attached to silicon atoms. Different additions of side chains can achieve significant variations in properties. Silicone o-rings have excellent heat, ozone and corona resistance and have good dielectric stability and resistance to many oils, chemicals and solvents. Silicone o-rings possess the best flexible property at low temperature but have low tensile strength and poor wear and tear resistance.
Cure System: Peroxide-Cured
Standard silicone o-ring compounds are usually peroxide-cured. Platinum-cured compounds offer better flexible properties and very low volatile matter. Platinum-cured silicone o-rings usually are applied in medical systems or other required low volatile matter. However, they need to be produced in a clean room and with a higher cost of platinum catalyzer, making them more expensive than peroxide-cured ones.
Silicone O Rings,Silicone Rubber O Ring,Silicone O Rings Based,Silicone O Rings Possess
Shenyang Guide Rubber Products Co.,Ltd , https://www.guiderubber.com